The information in this manual is subject to change without notice. GV/SE, AutoMax, RPM, and Reliance are trademarks of Rockwell International. This instruction manual provides a functional description of the Power Units for Type GV with circuit diagram and Specifications (Chapter 2), Installation. Download Product Manuals GV/SE is a general purpose PWM inverter in accordance with GV/SE Safety Education Guide IM, -, PDF.
|Country:||United Arab Emirates|
|Published (Last):||10 December 2008|
|PDF File Size:||20.32 Mb|
|ePub File Size:||17.35 Mb|
|Price:||Free* [*Free Regsitration Required]|
Reliance Electric GV3000 Instructions Manual
manua Locate pin 1 on jumper J Page 96 – Table 9. The coaxial cable must be run in continuous, rigid, conductive conduit. To reduce line disturbances and noise, motor lead length should not exceed 76 meters feet for any non-Reliance Electric motor or any non-inverter duty motor.
Terminal Block Assembly Blower Assembly Mounting The Drive Enter text from picture: Chapter 6 Installing Output Power Wiring Page 49 – Figure 4.
No additional filter installation is required.
List of Tables Table 2. Refer to figures 2. Verify that the DC bus voltage is zero by following the procedure in section 9. Chapter 9 Troubleshooting The Drive Don’t have an account?
Setting The Analog Output Tv3000 j17 Page 35 – Figure 3. Be sure input power to the drive corresponds to the drive nameplate voltage and frequency.
Reliance electric GV3000 Manuals
Page 55 Page 56 – Figure 5. HAPTER Completing the Installation This chapter provides instructions on how to perform a final check of the installation before power is applied to the drive. Regulator Board Description Don’t show me this message again. Chapter 8 Completing The Installation Page 31 Table 2. Wiring The Terminal Strip Step 3.
Page 94 – Table 9.
Comments to this Manuals Ggv3000 Name. Reconnect the motor to the drive. Wire the DC input power leads by routing them according to drive type. EN Section Title Protection against electrical shock 6. Refer to section 5.
Reliance Electric GV Manuals
Installing Mechanical Motor Overload Protection optional Do not route signal and control wiring with power wiring in the same conduit. On HP drives, close the outer cabinet door.
Be sure there is amnual clearance for air circulation around the drive. Page 75 Table 7. List Of Tables Recommended Power Wire Sizes Note that HP drives may be supplied with an optional AC disconnect. The required mounting hardware is supplied with the filter.
Use grommets, when hubs are not provided, to guard against wire chafing.
Mounting The Drive Use grommets, when hubs are not provided, to guard against wire chafing. Recommended Serial Communication Cable Lengths 3.
Wiring the Regulator Board Terminal Strip Identification of the protective conductor Warning signs and item identification Page 48 – Figure 4. The numbered items listed below correspond to the numbers used in figure 2. Page 4 Technical Specifications Page 42 – Table 3. Stopping The Drive